Please use this identifier to cite or link to this item:
|Title:||The performance investigation of a temperature cascaded cogeneration system equipped with adsorption desalination unit|
Energy utilization factor
Waste heat recovery
|Source:||Myat, A., Thu, K., Kim, Y.D., Choon, N.K. (2013). The performance investigation of a temperature cascaded cogeneration system equipped with adsorption desalination unit. Desalination and Water Treatment 51 (7-9) : 1900-1907. ScholarBank@NUS Repository. https://doi.org/10.1080/19443994.2012.714580|
|Abstract:||This paper presents the performance investigation of a temperature cascaded cogeneration plant, shortly in TCCP, equipped with an efficient waste heat recovery system. The TCCP or cogeneration system produces four types of useful energy namely (i) electricity, (ii) steam, (iii) cooling, and (iv) dehumidification and distilled water by utilizing single energy source. The TCCP comprises a Capstone C30 micro-turbine that generates nominal capacity of 26 kW of electricity, a compact and efficient waste heat recovery system and a host of waste heatactivated devices namely (i) a steam generator, (ii) an absorption chiller, (iii) an adsorption desalination system, and (iv) a multi-bed desiccant dehumidifier. The analysis is performed under different operation conditions such as heat source temperatures, flow rates of heat transfer fluids and chilled water inlet temperatures. The only single heat source for TCCP is obtained from exhaust gas of micro-turbine and it is channeled to a series of waste heat recovery heat exchangers to steam and hot water at different temperatures. Hot water produced by such a compact heat exchangers is the driving heat source to produce steam of 15 kg/h, cooling of 2 Rton, dehumidification of 2 Rton, and distilled water of 0.7 m3/day. A set of experiments, both part load and full load, of micro-turbine is conducted to examine the electricity generation and the exhaust gas temperature. It is observed that energy utilization factor could achieve as high as 70% while fuel energy saving ratio is found to be 28%. © 2013 Desalination Publications. All rights reserved.|
|Source Title:||Desalination and Water Treatment|
|Appears in Collections:||Staff Publications|
Show full item record
Files in This Item:
There are no files associated with this item.
checked on Feb 15, 2018
WEB OF SCIENCETM
checked on Jan 30, 2018
checked on Feb 12, 2018
Items in DSpace are protected by copyright, with all rights reserved, unless otherwise indicated.