Please use this identifier to cite or link to this item:
|Title:||Measurements and computations of contaminant's distribution in an office environment|
|Authors:||Cheong, K.W.D. |
|Citation:||Cheong, K.W.D., Djunaedy, E., Poh, T.K., Tham, K.W., Sekhar, S.C., Wong, N.H., Ullah, M.B. (2003). Measurements and computations of contaminant's distribution in an office environment. Building and Environment 38 (1) : 135-145. ScholarBank@NUS Repository. https://doi.org/10.1016/S0360-1323(02)00031-8|
|Abstract:||This paper investigates the dispersion of contaminants in an office environment using empirical and modeling techniques. The experiment was conducted in an environmental test facility with the mock-up of two typical office layouts. Layout 1 has two workstations located in the middle of the room and separated by a low-level partition, while Layout 2 has a low level-partition which separates the room into two halves with one workstation at each corner. The test facility, 6.6 m (L) × 3.7 m (W) × 2.6 m (H), is served by an air-conditioning and mechanical ventilation (ACMV) system which is capable of controlling the air temperature and airflow rates at the supply diffuser and extract grille. The contaminant's emission was generated by a constant injection of tracer gas, sulfur hexafluoride (SF6), via a 280 mm × 200 mm surface to represent the plane source. The concentration of contaminant in the chamber for both the layouts was measured and simulated using a gas analyzer and a computational fluid dynamic (VFD) program with the Re-Normalization Group k-ε model, respectively. In general, the predicted concentration of contaminant was in good correlation with the measured concentration. However, the predicted results were always marginally lower than the measured results. The contaminant's dispersion pattern was observed to be highly dependent on the velocity flow field. The layout of furniture influenced the airflow pattern and contaminant's distribution in the office. On the whole, Layout 1 was better than Layout 2 with a lower level of contaminant at the occupant's breathing zones. © 2002 Elsevier Science Ltd. All rights reserved.|
|Source Title:||Building and Environment|
|Appears in Collections:||Staff Publications|
Show full item record
Files in This Item:
There are no files associated with this item.
checked on Feb 20, 2019
WEB OF SCIENCETM
checked on Feb 20, 2019
checked on Feb 2, 2019
Items in DSpace are protected by copyright, with all rights reserved, unless otherwise indicated.