Please use this identifier to cite or link to this item:
|Title:||Three-dimensional numerical simulation of a hybrid fresh air and recirculated air diffuser for decoupled ventilation strategy|
|Keywords:||Air change rate|
|Citation:||Bin, Y., Sekhar, S.C. (2007). Three-dimensional numerical simulation of a hybrid fresh air and recirculated air diffuser for decoupled ventilation strategy. Building and Environment 42 (5) : 1975-1982. ScholarBank@NUS Repository. https://doi.org/10.1016/j.buildenv.2006.04.018|
|Abstract:||In conventional mixing ventilation air conditioning system, fresh air which has been polluted by recirculated air is supplied to occupied zone. Therefore, more fresh air which results in energy penalty needs to be supplied in order to keep good indoor air quality (IAQ) and thermal comfort. Some alternatives such as personalized ventilation air conditioning system can address this problem effectively by supplying fresh air directly into occupied zone. However, room layouts and visual effects will be influenced deeply because of extended air ducts. A new approach supplying fresh air directly by utilizing high velocity circular air jet without mixing with recirculated air is introduced. Objective measurements and computational fluid dynamics (CFD) tool are used to evaluate corresponding indoor parameters to verify that it can both supply fresh air into occupied zone effectively and avoid draught rating. It is found that the measured air velocities are within the limits (0.25 m/s) of thermal comfort standards, although they are close to the limits. Higher air change rate can be obtained in breathing zone than that in ambient air in the background area. The predicted results show unique distributions of airflow characteristics and are in fair agreement with empirical measurements. Different angles of recirculated air diffuser blades, different lengths and directions of protruding fresh air jets and different inlet velocities of fresh air are adopted for comparing the effectiveness and efficiency of this new ventilation strategy numerically. © 2006 Elsevier Ltd. All rights reserved.|
|Source Title:||Building and Environment|
|Appears in Collections:||Staff Publications|
Show full item record
Files in This Item:
There are no files associated with this item.
checked on Jan 12, 2019
WEB OF SCIENCETM
checked on Jan 2, 2019
checked on Jan 12, 2019
Items in DSpace are protected by copyright, with all rights reserved, unless otherwise indicated.