Please use this identifier to cite or link to this item:
|Title:||Space temperature difference, cooling coil and fan - Energy and indoor air quality issues revisited|
Indoor air quality
Supply air temperature
|Citation:||Sekhar, S.C. (2005). Space temperature difference, cooling coil and fan - Energy and indoor air quality issues revisited. Energy and Buildings 37 (1) : 49-54. ScholarBank@NUS Repository. https://doi.org/10.1016/j.enbuild.2004.05.003|
|Abstract:||In designing an energy-efficient air-conditioning system that also simultaneously addresses the needs of adequate ventilation and acceptable indoor air quality, several factors begin to play an important role. Among several others, the cooling coil, the fan and the temperature difference between the space and the supply air (commonly known as the Space ΔT) can be considered to be crucial. For a given space cooling load, the choice of a particular Space ΔT has an implication on the amount of supply air required, which further has an impact on the performance of the cooling and dehumidifying coil as well as the fan. Inherent in these implications are issues related to energy, ventilation and indoor air quality. This paper investigates these implications and quantifies them by considering a hypothetical building in a tropical climate and subjecting the design to several parametric variations involving different Space ΔTs for a given space temperature and humidity condition. The total power requirements, comprising additional cooling, reheating and higher fan power, for a design involving a Space ΔT of 5°C can be as high as a factor of 2.2 of the total power for a design with a Space ΔT of 8°C. The implication of higher supply air flow rates on duct design is qualitatively discussed. For a given space cooling load and a given Space ΔT, the implication of increased design ventilation rates to address part-load ventilation requirements can lead to an additional installed cooling capacity of 17.5%. Finally, emerging technologies that are aimed at addressing both energy efficiency and IAQ are discussed. © 2004 Elsevier B.V. All rights reserved.|
|Source Title:||Energy and Buildings|
|Appears in Collections:||Staff Publications|
Show full item record
Files in This Item:
There are no files associated with this item.
checked on Aug 14, 2018
WEB OF SCIENCETM
checked on Aug 6, 2018
checked on Aug 3, 2018
Items in DSpace are protected by copyright, with all rights reserved, unless otherwise indicated.